ШРПО-12 cabinet is designed for utilization on the floors in high rising building and serves for optics distribution, using GPON technology.
Cabinet is protected from unauthorized access; it has one door and is wall-mounted. Total cabinet capacity is up to 36 SC optical connectors (4 are used for splitters entries connection).
Welding number is up to 48.
It is possible to assemble PLC optical splitters with divisions from 1/4 to 1/32 both in compact and box designs.
There are 10 entries in the cabinet (2 both at the left top and bottom and 1 entry at the right top and bottom) for up to 32 mm diameter tube for incoming distributing and subscribers’ cables.
Cabinet overall dimensions (HхWхD) – 335х395х100 mm.
Cabinet is protected from unauthorized access. IP 43 protection class according to State Standards 14254-96.
Paint type – polymeric coating, RAL 7035 РЕ, shagreen, rough structure, and glossy.
Metal thickness is 1, 2 mm.
Maximum number of SC connectors– 36.
Maximum number of welding – 48.
Cable entries number – 10.
Maximum number of incoming cables with ОКЛ type ribbon armour– 12 ( 3 cables per one entry).
Splitter maximum capacity – 1/32.
Splitters maximum number:
a) 4 units-1/8;
b) 2 units-1/16;
c) 1 unit-1/32.
Maximum number of ОК-24 cassettes for 24 fibers– 2 units.
Weight – 5,7 кg.
Operating temperature: from 400С to -100С. Climatic design is of У 3 category according to State Standards 15150-69.
Cabinet is divided into 3 parts for convenience: cabinet’s back wall, inner part of folded panel and front part of folded panel.
On the back wall there are holders for strength elements (up to 10 strength elements), special place for optical modules laying and cassettes for welding.
There is a bus for armour jacket optical cable earthing at the bottom. On inner side of the folded panel there is tray for PLC splitters and special place for splitters incoming and outgoing reserves laying. On the front panel there are simplex SC connectors. There are 2 rows of connectors there, 18 connectors in a row. The rows are separated. 1, 18, 19 b 36 connectors are visually separated and provide only splitters connection. Pigtails or splitters exits are connected from inner side; subscribers’ patchcords and splitters entries are connected from outer side.
Folded panel is fixed in the center by means of captive screw.
There are 10 entries in the cabinet (4 entries – 2 at the top and at the bottom on the left and 1 at the top and at the bottom on the right for standard solutions when tubes are vertical; 4 entries - 2 on the right and 2 on the left if it is necessary to enter the cable from one side). Т-shaped (turning according to cable entry) cable fixing elements are placed by each cable entry and provide fixation of up to 3 cables by means of metal clips.
Cabinet has a single door with 2 locks.
ШРПО optical distribution building entrance cabinet, model 012 with SC/APC optical connectors, 32 ports with single-mode SC/APC 28 pigtails, 2 cassettes for optical fibers welding, with 28 protecting sleeves, 1 splitter with 1/16 division and 1 splitter with 1/8 division.